The Alfa Laval Aalborg Micro is a uniquely compact boiler/economizer designed for waste heat recovery from a vessel’s auxiliary engines.
The cost-efficient way to meet your need for steam
- Extremely compact, plug-and-play design for easy retrofit
- Short payback time through up to 25% fuel savings
- Reduced wear and maintenance on the oil-fired boiler
- Short start-up time (2 minutes)
- Low media volume and inertia that contribute to high uptime
Reduce fuel consumption, ensure redundancy and optimize your steam plant. Let waste heat cover your need for steam – and future-proof your vessel for the 2020 regulation and beyond.
The Aalborg Micro is a game-changing solution with a tremendous potential in fuel savings - small and easy to install.
By reclaiming heat from auxiliary engine exhaust the Aalborg Micro gives a remarkable opportunity for saving fuel and maintenance cost. A typical retrofit installation saves enough fuel to reach payback in 1-2 years - and it is not only money being saved. CO2 emissions are reduced by around 900 tonnes annually.
Only a portion of the fuel energy released by marine engines actually goes to propulsion. A large amount of it escapes as heat, and it makes sense to reclaim as much of this energy as possible. This is true not only for main engines, but for auxiliary engines as well.
Steam produced with the Aalborg Micro can support or fulfil steam needs in port, but it can also serve other functions. For vessels whose long-stroke main engines produce cooler exhaust, it can provide a needed steam boost during a voyage. Vessels that use blended fuels from 2020 onwards may also require additional steam, since these fuels will need to be stored at a higher ambient temperature – even if their pumping temperature is lower.
The Aalborg Micro is installed after the vessel’s auxiliary engines (or small main engines). When the exhaust gas passes over the Aalborg Micro heating surface, the waste heat energy in the gas is absorbed for the production of hot water or steam.
The Aalborg Micro is not designed with its own steam space. It is used in connection with one or more oil-fired boilers, which act as the steam/water space. Forced circulation provides the Aalborg Micro with water at saturation temperature from the oil-fired boiler(s). The circulation pumps are located between the oil-fired boiler(s) – or a separate steam drum – and the Aalborg Micro.
In the Aalborg Micro, heat from the engine exhaust gas is transferred to the water side by convection. The generated steam/water mixture is then discharged into the steam space of the oil-fired boiler(s), where the heavier water particles separate from the steam.
Steam plant optimization through waste heat recovery from auxiliary engines
Economizer for the oil-fired boiler
Full redundancy for existing steam plant
How it works
- Capacity: 500 kW up to 5 MW
- Weight (incl. insulation): 400–3900 kg
- Diameter (incl. insulation): 950–1870 mm
- Height (incl. insulation): 1700–2800 mm
- Connections: Welded
- Insulation: 150 mm
- Media inlet/outlet header: DN100
- Exhaust inlet/outlet header: DN450 to DN1000
- Maximum inlet temperature: 535°C
- Minimum outlet temperature: 130°C
- Pressure loss: <4500 Pa
- Maximum pressure: 39 bar(g)